View this film to understand the potential ramifications of operating a subsea electrical system with low IR. In addition, Neil Douglas, Managing Director at Viper Innovations, explains the implications of copper loss.
WHAT IS CONSIDERED LOW IR?
A LIM device will provide continuous monitoring of the IR for the overall system. Most LIMs have the ability to set an alarm and subsequently to de-energise the subsea circuit at predefined IR thresholds. In practice, operators wish to keep the system running as long as possible, even in the presence of degraded IR, and would only shut down if a dangerous or unsafe condition occurred. Hence the trip threshold tends to be reduced to the minimum, and then ‘bypassed’ when that minimum threshold is reached.
The main safety device in such circumstances is the overload circuit breaker, which will be triggered if the leakage current plus the normal load current together exceeds the safety trip level. This is generally a function of the maximum current delivery capability of the Electrical Power Unit (EPU). Overload circuit breakers are designed to trip when a large current flows, usually due to a short circuit, and the ratings of the circuit breaker are ultimately chosen to respond to transient loads to make the circuit safe and to avoid damage to the surface power supply. The increased load current due to subsea IR reduction tends to be a long-term, steadily increasing value, which only triggers the circuit breaker when significant current flow is registered.
Operationally, the subsea load can be sustained in the presence of a considerable reduction in IR.
An alarm to alert the operator that there is a low IR issue should be set at a level no less than 200kΩ but operation can continue. With such an alarm, the operator should be aware of the consequences of continuing to operate; specifically in respect of long-term damage to the electrical conductors. However, for safety, a trip setting must be calculated dependent upon the operating voltages of the system. IEC (International Electrotechnical Commission) standards provide figures for the human body impedance and British electrical safety standards provide the leakage current limits for human safety. These factors coupled with the operating voltage can be used to correctly and accurately set the trip threshold of the LIM. This setting will, therefore, be bespoke to every system and should not be guessed or left at the factory delivered default on the LIM.
WHAT ARE THE CAUSES OF LOW IR?
Such water ingress to subsea electrical cables and connectors is the dominant cause of electrical faults. This results in an increase in leakage current and a low insulation resistance (Low IR) alarm. Continual insulation degradation eventually leads to failure of the circuit. When the seawater penetrates the insulation and comes into contact with the copper conductors, a leakage current flows through the seawater which is a good conductor of electricity – i.e. the sea water has a low electrical resistance. Sometimes the drop in insulation resistance is sudden, but usually, it drops gradually, giving plenty of warning, if checked periodically.
WHAT IS COPPER LOSS?
The principle of insulation monitoring is to apply a voltage between the copper conductors in a cable and earth and measure the resulting current that flows. Using a LIM to monitor IR degradation in a cable which is submerged in seawater will cause damage to the copper conductors at the point where the conductor insulation is damaged.
Whilst copper is lost as a result of using a LIM, the loss of copper is significantly greater when there is a line voltage on a cable which has suffered from IR degradation on both wires. Operators should recognise that applying power to an umbilical or cable with low IR will result in corrosion of the copper conductors.
In any given degraded cable, the rate of copper loss is directly proportional to the magnitude of the leakage current. Clearly the lower the value of the insulation resistance the higher the rate of copper loss.
The Viper V-LIM has been designed to reduce the copper loss when compared with competing IMDs on the market, and in addition, the Viper V-LIM can also be reconfigured to reduce the applied voltage and therefore leakage current in low IR conditions – further reducing any copper loss.
Besides replacing failed cables and umbilicals, the only real solution to almost eliminate entirely the copper corrosion is to activate V-LIFE on the Viper V-LIM. The V-LIFE process blocks any paths that the seawater will take to reach the copper and thereby reduce, by orders of magnitude, the corrosion of the copper and subsequently extend the life of the subsea electrical infrastructure.